- Home /
- Choosing an MVHR unit
Choosing an MVHR Unit
There are a lot of differences in heat recovery units from performance output, physical size, orientation, controllability, cost and types of heat exchanger.
As it is impossible for any one unit or manufacture to provide a solution for all houses so we have over 50 MVHR units available to professionally provide a bespoke solution that would be suitable for your project to provide a quiet and efficient system.
To achieve a quiet and efficient system it all starts here in design and specification, you can either:
- Contact our trained technicians who will provide a list of suitable units from details given or by you providing a set of plans
- Follow this guide and check our easy to use product selector to ensure that you have the best solution
Each manufacture has their own area of expertise
- Vent Axia – excellent controllability and reliability
- Airflow Adroit – Interactive control and Passive house approved
- Airflow Basic – Great value for money
- Expelair 180 – all features and fits into kitchen cupboard
- Vortice – Very quiet and good range of sensors
- Polypipe – good digital controller and excellent value
- Nuaire – Ideal for social housing projects with simple operation
Heat exchangers for heat recovery units -
We always specify Counterflow heat exchangers for domestic properties. There are two types of heat recovery (Counterflow and rotary wheel) 90% of domestic heat exchangers and all UK manufactured units are now Counterflow due to energy efficiency, heat recovery efficiency and the major fact that the air streams do not mix.
Rotary heat exchangers are better suited to commercial applications such as offices due to slight humidification of the air. (Moisture collected can enter incoming air stream -not a good idea on a residitial property) and the larger airflow possible through rotart exchanger
Determine heat recovery airflow requirements -
Basic guide for unit selection!
First check the amount of air that you require the system to supply and extract
The airflow bust be the greatest of either system 1 or 2
simply add the number of wet rooms together eg
This means that you need to extract @ 45 l/s and you should be looking for a unit that can acheave an extraction of 75 l/s
eg a 5 bedroom house with a floor area of 200 m2 would need 66 l/s (200x hight of rooms of 2.4 m =480 m2 % 2 = 240 %3.6 = 66)
this means that you need to supply @ 66 l/s and you should be looking for a unit that can acheave a supply rate of 110 l/s
Choosing the size of heat recovery unit ! -
For best practice choose a unit that runs at less than 70% of total required output on boost. A MVHR unit should not run at 100% output.
Heat Recovery Efficiency -
From 2018 all new heat recovery system have a EPR (energy performance rating) and we recommend that all units have a minimum of an A rating
All quality heat recovery systems are also rated by BRE (SAP Appendix Q) and have independent performance results available to everyone.
Choosing the correct ducting for a heat recovery system -
A heat recovery system is only as good as the ductwork. There is no point in buying the most expensive unit just to install sub standard ducting.
There are a number of options in ducting and all can impact performance. The main factors being:
We always recommend a radial ducting solution for the quietest and most efficient system